|no false alarms Mil-Ram patented Chlorine Electrochemical sensor technology|
|Self-Calibration adjusts span monthly based on sensor life curve|
|Auto-Gas Calibration, non-intrusive, hands-free, magnetic switches|
|Not affected by temperature -40 deg C to +50 deg C, stable by design|
|LCD display - 12 characters x 2 lines. Provides user interface with magnetic switches - no dip switches|
|Offsite sensor calibration with memory chip embedded in sensor|
|Peak value, 15-min. TWA, Remaining Sensor Life, Replace Sensor indication and number days since last gas calibration|
|Optional Relay Module in same enclosure with low, mid, high and fault relays|
|Can be used with Mil-Ram's Wireless Telemetry System|
|Available suitable for use in SIL 2 environments|
|Continuous advanced Diagnostics|
|Detection Range||0.0-5.0 PPM (parts-per-million)|
|Response Time||< 45 sec to 90% of final reading|
|Recovery Time||< 30 sec. to 90% recovery|
|Temperature Range||-40 deg.C to +50 deg.C|
|Humidity Range||10-95% RH, non-condensing, continuous|
|Zero Drift||< 0.1 PPM|
|Power Requirement||12V or 15-30VDC; 1.08W @24VDC|
|Output||4-20mA linear. Optional Modbus RTU. Optional Relays; low, mid, high & fault.|
|Long life||>3 years typical under normal operating conditions|
Chlorine Cl2 is a greenish-yellow gas with a pungent, irritating odor. Chlorine is classified as a strong oxidizer. Gas density is 2.47 (relative to air). Units conversion: 1ppm = 2.90mg/m3. Chlorine is a nonflammable gas. CAS#7782-50-5.
Threshold limit value (TLV): 0.5ppm, 1.5mg/m3 TWA; 1ppm, 2.9mg/m3 STEL.
Recommended Exposure Limit (REL): 0.5ppm TWA; 1ppm STEL.